How to Clean the Central Heating System.
Is your radiator giving off a very bad smell of bad eggs or similar when you bleed them of air? (the removal of air via the air vent) Then this could probably be a build-up of a chemical called hydrogen sulphide in the water.
Hydrogen Sulphide which can build up in the heating system not only causes a bad smell but will cause corrosion and sludge within your central heating system over time and will need removing.
A few good brands of central heating cleaner and inhibitors available are Sentinal, Fernox or Adey that will be perfect for the job, but you will need to drain and flush out the old water from the system first.
Cleaning the Central Heating System
Before you introduce a new product to the central heating system, we recommend you fully drain the heating system of water. This will remove the loose deposits and sludge suspended in the water.
Draining Down the Water in the Central Heating System
First things first, turn of the power to the boiler and controls. Allow the system to cool. If you have a vented system close the supply to the feed and expansion tank in the loft.
When you are ready to drain the system, you must find the drain cock on the pipework. This is normally found on a radiator by a doorway on the lowest part of the system. Run a hose to an outside drain and attach a clip to secure the end of the hose to the drain cock. Open the air vents at the top of the system to allow the water to drain away. Remember to close all vents once your system is empty.
Refilling the Central Heating System
Close the drain valve and fill the system. Remove the hose from the drain cock. With a vented system open the water supply to the tank in the loft which will allow the water to flow back into the system.
With a sealed system you need to locate the filling loop and open the valves to allow water into the system paying attention to the pressure gauge. The recommended pressure for heating systems is normally 1 bar.
You will now need to vent each radiator by opening the bleed valve to release the trapped air. Always start with the lowest level radiator and work your way to the top of the house. This reduces the chance of trapping air in the lower part of the central heating system.
Adding the System Cleaner
Check the manufacturers details on the correct amount of chemical to use in the system. The method on how to add the cleaner will determine what system you have. For an open vented central heating system, you can easily add the chemical when filling up via the feed and expansion tank.
For sealed central heating systems, the chemical comes in pressurised cartridge and is required to be connected to the air vent on a radiator via a special attachment hose. This solution is injected into the heating system.
Turning the Central Heating System Back On
Switch on the power to the boiler and controls then turn your thermostat up. Allow the boiler to operate at its normal temperature for at least 1 hour. This will ensure the cleaner can circulate and break down the deposits inside the radiators and pipework. It may be necessary to leave the cleaner in for longer depending on how dirty the system is. 7 to 28 days in some cases. This will allow more time to break down the stubborn sludge and scale into the suspended water.
Drain and Flush the Central Heating System
Once the cleaner has had enough time to work it is suggested to flush out the chemicals until the water runs clear. Once this is done then refill and add inhibitor to protect the system for the future and reduce the build-up of sludge and scale. This will also prolong the life of the pump valves and other moving components in the system as well as reducing the likelihood of boiler break down.
Something You Must Know
Systems that have larger quantities of sludge and scale may require a power flush with the use of magnetic filters. This is a more effective solution to the fill and flush method written above and would be advised if you have a high efficiency boiler. All new high efficiency boilers have smaller water ways in their heat exchangers and can easily become blocked (by debris moving through the central heating system) if the right precaution are not taken. This is where it becomes more complicated and expert heating engineers are suggested to carry this type of work out to your central heating system.
Our engineers have been trained on all types of heating systems and have the right equipment to remove the maximum amount of sludge and scale from your central heating system allowing the circuit to become free of debris and increasing the flow heat and efficiency of the boiler.